Email notification offers the possibility
for the user to re-direct UPS alarms towards an e-mail system or mobil
On the right side of the page, the events which can be notified, appear.
Two events are selected by defaut for notification. At any moment, the default
selection can be setted with the button Set default.
On the left side of the page, up to four Mail recipients can be configured
to receive mails from the card. Each mail recipient has its own events set,
which can be selected on the right side.
The parameters for each recipient are :
Recipient is the email address of the person or service you wish the card to send a mail to.
Default value is email@example.com.
E-notify: this parameter enables communications to the Eaton eNotify Monitoring and Diagnostics Service. NOTE: Available only for clients with a valid eNotify Service Contract.
Attached files on Event : Selected log files
(Measurements, Event log, system log or environment log) will be attached to the mail sent.
Periodic report: the card can send a mail, containing all attached files,
to the recipient every x days at x hour .
Enter the day of next report to select the date of the
first report. After receiving this one, the day of next report will
display the remaining time before the next report.
The first time this function is used, also enter the day of next report
in the month you want to begin to send the periodic report.
Also Next happen day can be used after to check the next day the periodic report
will be sent.
Test is a manual way to immediately send a mail to the mail recipient.
It's for checking the email transmission, notably access to the SMTP server
fails. A message will be logged into the system log in both cases : success
The event message part in the subject and into the message of the mail is replaced with a test message.
Email Message Settings:
Personalize the email content and objet.
The Save button allows to save the modified settings for the selected recipient.